View and Download Dixell XR40C installing and operating instructions online. Digital controller with defrost management. XR40C Controller pdf manual. Dixell-XR40C – Download as PDF File .pdf), Text File .txt) or read online. DIXELL XR40C CONTROLLER, XR40CX-4N0F7. Order from Heritage Parts the leading online provider of OEM commercial kitchen replacement parts.
|Published (Last):||9 May 2010|
|PDF File Size:||12.24 Mb|
|ePub File Size:||7.53 Mb|
|Price:||Free* [*Free Regsitration Required]|
At the end of defrost dripping time is started, its length is set in the FSt parameter.
We will be unable to respond to your comments without your email address. The Leading Distributor of Restaurant Supplies and Equipment Based in Lancaster, PA, WebstaurantStore is the largest online restaurant supply store serving food service professionals and individual customers worldwide.
With thousands of available products and over 5. Our focus is your convenience — order online from your laptop, desktop, or smartphone dixelo hours a day, 7 days a week. Enter text from picture: Page of 4 Go. To print the manual completely, please, download it.
Page 2 OE Evaporator probe calibration: To see the kind of alarm, the max min reached temperature and alarm duration. In case of applications in industrial environments, the use of mains filters our.
Consider the maximum current which can be applied to each relay see. Using cookies and identifying data such as IP address and the type and version of your browser help us improve our website’s navigation and provide more personalized services to you.
Got it, continue to print. To see the last temperature alarm happened; in programming mode it.
electronic controller DIXELL XR40C-0R0C3 402158
If you’ve used this product, simply log in and share your text, video, and photo reviews of it. The xxr40c is performed according to the temperature measured by the.
Push and immediately release the SET key or wait for 5 seconds to display. To confirm the operation, the “rSt” message starts blinking and the normal.
Then the instrument displays the temperature once again.
electronic controller DIXELL XR40C-0R0C3 | horecatiger
To display target set point; in programming mode it selects a parameter or. Don’t have an account? If you wish to submit your comment without an email address, please click “Give Feedback” Email Address. Then the “tiM” tiMe message is displayed, followed by the “Duration” in.
Don’t show me this message again. Based in Lancaster, PA, WebstaurantStore is the largest online restaurant supply store serving food service professionals and individual customers worldwide. OE Evaporator probe calibration: Comments to this Manuals Your Name. It has 2 relay. The instrument is fully configurable through.
High temperature alarm fault. For more information, go to www.
DIXELL XR40C INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
Push the SET key for more than 2 seconds to change the Set point value. Comments Email Address We are only able to reply to comments xr04c include an email address.
Over the years we have expanded our selection of wholesale supplies and commercial equipment to include healthcare, educational, and hotel supplies. MdF and two defrost modes: Each LED function is described in the following table.
The instrument shall not be used for purposes different from those described. Do not expose to water or moisture: Two defrost modes are available through the “tdF” parameter: Add to my manuals Add.